3200VS Temperature & Humidity Performance
We tested CellarPro's 3200VSi wine cooling unit for 24 hours by heating the condenser environment to 110°F. Despite the grueling heat, CellarPro's 3200VSi was able to maintain temperatures at 55°F and relative humidity at 62% inside the wine cellar. (2)
- The cooling unit was tested in a 750 cubic foot wine cellar with R-13 rigid foam insulation and a moisture barrier
- The wine cellar was filled with approximately 7500 bottles
- The CellarPro cooling unit was set to maintain 55°F (53°F "off" and 4°F Temperature Differential) (1)
- The temperature measurements inside the wine cellar were taken at the far wall (approximately 10' from the cooling unit)
1) CellarPro cooling units provide maximum flexibility for controlling the environment inside a wine cellar. Rather than selecting a single temperature target, CellarPro users designate the lower and upper temperature settings during which the cooling unit cycles off and on. In the test charted above, the CellarPro cooling unit was set to cycle "off" at 53°F, and cycle "on" at 57°F (55°F average.)
(2)The short spikes reflect the cooling unit's auto-defrost cycle.
We've put together some basic resources to guide you through the process of choosing a cooling unit and building a cellar.
You need this number to choose the right cooling unit. We'll figure it out for you.
To contact our support team, email us or call 877.726.8496.